The science is unparalleled.
Ti-DOX HydroxylizAire simultaneously destroys airborne germs and toxins and is safe to use in occupied spaces.
8-Way Cleaning Technology
01. Chamber Design
The Ti-DOX HydroxylizAire chamber attaches to any forced air ventilation system without restricting airflow.
02. Hydroxyl Radicals
The Ti-DOX HydroxylizAire has been engineered to safely generate hydroxyl radicals, which attack germs and toxins in the air that flows through the chamber.
The UVC lamp generates heat, which helps break down the protein envelope that protect germs.
04. UVC Light
UVC, a type of ultraviolet light, works to destroy germs. In addition to heat, UVC activates a photocatalytic coating to generate hydroxyl radicals.
The design and internal coating of the Ti-DOX HydroxylizAire chamber ensures that germs and toxins are constantly close enough to the UVC light.
06. Direct Light Path
The UVC light always reaches the airborne germs, toxins, and photocatalytic coating no matter where they are in the chamber.
07. Exposure Duration
Air moves back and forth across the Ti-DOX HydroxylizAire chamber to ensure any germs and toxins are exposed to the UVC light and hydroxyl radicals long enough to be destroyed.
08. UVC Light Dosage
The Ti-DOX HydroxylizAire balances the first seven design features to provide an effective dosage of UVC light to destroy germs and toxins in the air that flows through the chamber.
Improve your indoor air quality.
Destroys airborne germs and toxins
Cleans the air throughout any indoor environment
Affordable peace of mind
Our patented based 8-way design simultaneously destroys germs and toxins with minimal maintenance.
HydroxylizAire is for indoor installation on forced air duct system only.
Select a suitable method to firmly mount the HydroxylizAire
Cut duct opening 75mm – 100mm for HydroxylizAire inlet connection, on hot air duct downstream of furnace or HVAC fan
Cut duct opening (75mm – 100mm) for HydroxylizAire outlet connection, on cold air duct upstream of furnace or HVAC fan
Attach 100mm male flange duct fittings to HydroxylizAire inlet/outlet openings and to ventilation duct openings
Install supplied 100mm duct pipe (flexible or fixed) between duct openings and HydroxylizAire inlet/outlet connections
Multiple HydroxylizAire's may be connected in parallel and/or in a series to achieve additional flow-through volume
HydroxylizAire can be installed vertically or horizontally or angled
HydroxylizAire internal flow can be in either direction
Allow adequate space (min. 965mm/38”) to install/remove the lamp
Ensure power cord and lamp cables are properly connected to ballast
Ensure electrical supply is disconnected and ballast de-energized prior to any cord/cable connections and/or lamp installation/removal
It is recommended that a filtration device be installed upstream of the HydroxylizAire inlet for capturing particulate matter (PM)
After connecting the power cord to power outlet, breathe easy knowing you're breathing the cleanest indoor air.